Conventional convectors and radiators need relatively high flow temperatures to provide good heating coverage and do not consume energy as efficiently as they could.
Panel heating systems, for example underfloor heating, can help to save energy and heating costs and be operated at low flow temperatures.
However, panel heating is expensive and difficult to engineer when renovating old buildings or upgrading an existing system.
Fan convectors have a specially designed heat exchanger which is ideal for heating living spaces in an energy-efficient manner when combined with low temperature heating systems in an older building. The low-noise fans distribute heat evenly to warm the room for optimum comfort.
When installed with a reversible heat pump this convector can be used for cooling rooms and buildings and ensures that the desired temperature is reached quickly with its powerful energy output.
The new SmartRad series for heating and cooling combines a sophisticated design with advanced technology.
The desired room temperature can be set using the electronic thermostat.
The convector electronics compare the set temperature and room temperature and adjust the three fan levels automatically to reach the set temperature.
If the difference between the temperatures is high, the convector switches to the highest fan level. As soon as the room temperature begins to reach the set temperature, the air flow is reduced in stages and switches off automatically when the set temperature is reached.
The maximum fan level can be pre-configured manually, for example to avoid adjusting the fan level in sleeping areas.
|SRX 070CM||SRX 120CM||SRX 160CM|
|Heat output 55°C/47°C1||kW||0,57 / 0,74 / 1,07||1,32 / 1,63 / 1,95||1,72 / 2,25 / 2,82|
|Heat output 45°C/40°C1||kW||0,42 / 0,54 / 0,78||0,96 / 1,2 / 1,42||1,25 / 1,63 / 2,05|
|Heat output 35°C/30°C1||kW||0,22 / 0,27 / 0,4||0,49 / 0,6 / 0,71||0,64 / 0,8 / 1,02|
|Cooling capacity2 7°C/12°C1||kW||0,37 / 0,41 / 0,6||0,77 / 0,96 / 1,13||0,95 / 1,23 / 1,51|
|Cooling capacity2 10°C/15°C1||kW||0,27 / 0,31 / 0,45||0,56 / 0,7 / 0,82||0,69 / 0,9 / 1,14|
|Volume flow fan level1||m³/h||60 / 125 / 228||120 / 225 / 410||160 / 300 / 540|
|Sound pressure level at a distance of 1 m1||dB(A)||27 / 38 / 47||27 / 38 / 47||27 / 38 / 47|
|Width x height x depth||mm||503 x 530 x 145||740 x 530 x 145||911 x 530 x 145|
1) Values for low, medium and high fan levels
2) Total cooling capacity (sensitive and latent)